Schako Volkom. The round volume flow control
Schako Volkom, mechanically, constantly and subsequently adjustable.
The volume flow controlSchako Volkom operates automatically without auxiliary energy. The air speed moves the centrally mounted regulating flap. A control unit with control curve, damper and spring is mounted on the outside of the housing. The desired flow rate is set directly at the installation location. The control unit is protected by a cover. The controller can be installed in any mounting position. The set volume flow is then constantly controlled by the Volkom. The Volkom is installed in a circular duct, whereby subsequent adjustment of the flow rate is possible because access to the controller mechanism is provided.
The housing tightness corresponds to class B, DIN EN 1751
To enable subsequent adjustment of the air volume, inspection openings of sufficient size and number should be provided by the customer.
Advantages it constants Schako Volkom
- regulation of air outlets and simple adjustment
- Maintenance-free operation
- For Fields 24 in stock
Can be installed irrespective of position
Volume flow setpoint adjustment infinitely variable from outside at the Volkom possible.
The damper element and control unit are located outside the air flow, making the Volkom less susceptible to contamination.
building material class B2, DIN 4102
Fields of application
In all supply and exhaust air systems, to regulate a constant volume flow rate
Attention: The Volkom controller works with mechanical operating principle. Mechanical or manual intervention in the controller is not permitted. If a high flow rate setting is selected, the damper blade must not be closed manually. Otherwise, the control mechanism will be adjusted, resulting in a loss of control accuracy. The area of application must always be taken into account. If the permissible range of application of the Volkom is exceeded, this leads to mechanical overload and also to a loss of control accuracy. If a correspondingly higher air volume is set on the Volkom while the system is running, the control mechanism must be reset.